Warmth Cool Systems can be tried to quantify continuous BTU Capacity and EER. It is basic to discover a 3 ton, 13 SEER, Heat Cool System just delivering 2 tons and 8 SEER. We have discovered new establishments with this issue. Heating and Cooling
On the off chance that the framework is more than 12 years of age it might have lost huge limit and effectiveness.
Around 70% of your warmth and cool aeration and cooling system unit limit is utilized to bring down the temperature of the air. The staying 30% limit is utilized to expel mugginess or dampness from the air. For instance a 3 ton unit ought to have an aggregate limit of 12000 btu’s for each ton or 36000 btu’s. Of the 36000 btu’s, 24000 btu’s would bring down the temperature of the air and 12000 btu’s would expel dampness from the air. So as to quantify add up to limit, we should gauge both.
An ordinary thermometer will quantify the air temperature entering the arrival of your AC and the temperature of the colder air can be estimated at the principal supply vent. On the off chance that you increase the distinction in temperature by 1.08 btu for each cubic foot of wind current created by the Heat Cool System, you have the limit measure that brings down the temperature. This measure is called sensible warmth.
Another thermometer called a psychrometer or hygrometer is expected to gauge the stickiness that is expelled by the ventilation system. A psychrometer is a typical thermometer with a wet cotton sock over the knob. The temperature perusing called wet globule temperature can be changed over to an esteem demonstrating the temperature and grains of dampness noticeable all around. This esteem is called inert warmth and enthalpy. You can buy or make a wet knob thermometer. An exceptionally exact computerized hygrometer that measures % relative stickiness can be bought for around $100. Utilizing an enthalpy outline or enthalpy adding machine accessible on the web, you can change over your estimations to btu’s. It is critical to gauge wet globule temperature inside one tenth of a degree F.
The more troublesome measure to get is the measure of wind current in cubic feet every moment (CFM). An instrument called a vane anemometer can be utilized as can an instrument to quantify static weight. Guideline recordings for estimating wind current in CFM can be found on www.youtube.com
Computing absolute Btu’s includes estimating wind current and wet knob air temperatures in and into an adapted space. Add up to Btu’s are ascertained utilizing the recipe:
Add up to Btu = 4.5 X CFM X Enthalpy Change
The 4.5 factor speaks to the heaviness of 1 cubic foot/minute (CFM) of standard air every hour.
CFM is the aggregate supply wind current entering the working from the framework.
Enthalpy change is estimated utilizing a hygrometer and changing over the readings to Enthalpy.
Idle eat = Total Heat – Sensible Heat
Air and warmth can spill into the framework between your temperature readings and the indoor cooling curl. On the off chance that this happens, your figuring will show the cooling conveyed to the space and not the cooling delivered by the AC unit.
You can likewise decide hardware wind stream via painstakingly estimating fan static weight, at that point plotting the fan CFM in view of the producer’s fan information
An enthalpy change of around 6 is ordinary.
Wind stream majorly affects framework execution. It must be estimated precisely with top quality instruments and methods.
A stickiness level of 90% or more from the supply side of the framework is normal. As the air is cooled is can hold less dampness.